When we bought the house we learned it had a fairly new Bryant furnace installed. The previous owner upgraded from an electric furnace a few years ago. When we had an HVAC guy over for an AC quote he mentioned it was a good two stage furnace, better than the one we had in Bothell. Ok, I didn’ really think about until a recent discussion with some colleagues at Microsoft.
When inspecting my connections of my NEST, I assumed the R, G, C and W1 wires needed to be connected. C is for power, the other ones for the fan and heater. In my previous home the Y was used for the airconditioning. I don’t have one in this house yet. Although if you connect the wire to the Y on the backplate of the NEST, the nest assumes you have a AC connected.
Since you need to hook up the W2 on your thermostat to work with a two stage furnace to make it work. I connected the spare wire to the W2 on the backplate. The NEST gives you a message the wiring is changed and now a two stage heating system is connected. That looked promising. One of my colleagues mentioned it might not be smart to just randomly connect wires and he was correct of course. So disconnected the W2 wire from the NEST and took a better look at my furnace. (In the picture below the W2 connector is lefr from the blue wire)
Great thing about internet is you can find all kinds of information. I happen to have a Bryant 355MAV042080F model. Some googling on Bing pointed me to the user manual and the installation instructions. Cool.
Also on the inside there are some schematics of the furnace.
After some reading and inspecting the furnace after opening it up I saw the yellow wire wasn’t connected at all. So i hooked it up to the W2 connector, checked if the SW2 switch was on (which was). Hooked the wire up on my NEST and voila, two stage furnace worked. Yellow light came on when HIGH HEAT was switched on (just cranked the NEST up to 90) and the green light came on when in LOW HEAT mode (when I switched the NEST to 1 degree more than the current temperature).
No idea why the W2 wire wasn’t hooked up. The original Honeywell thermostat supports this system as well. I took some pictures before I installed the NEST and it wasn’t connected when I removed the old thermostat.
So I am kinda proud of myself I increased the efficiency of our thermostat.